Fire pump maintain and maintenance of pump manufacturers in china
Fire pump maintain and maintenance by pump supplier of eu-flo
The fire pump been checks every shift and guarantees that the power supply and circuit of the fire protection system are unobstructed, and the electrical well equipped.
Every shift turning pump by hands, to checking the coupling should be light and heavy be balanced, no abnormal noise and make record.
Check the Lubrication oil level in the vacuum installation on the 5th, 10th, 15th, 20th, 25th and 30th of each month. The oil position is at the center line of the oil window or slightly lower than the center line; start the fire truck fire pump, Check the fire pump water in coming time and make a record. The 1# and 2# pumps run for 15 minutes, and the 3# and 4# pumps run for 5 minutes.
Check the operation of the float assembly after the pumps is started. There should be no water in the exhaust hose. If there is water, it is necessary to change the float seal.
After the pump is started, check whether the sealing body can be tightly sealed and the exhaust air can be normal.
Check the packing seal level after the pump is started. The leakage should not exceed 10-30 drops/min.
Regularly check the Lubrication oil of all parts of the pump to ensure that the lubrication system works normally.
Regularly check whether the joint parts can be tightened or not.